Price (Per FT.)
Aluminum 600V URD cable is designed for use in secondary distribution circuits, where installed in duct or direct burial applications. Maximum operating temperature is not to exceed 90°C in wet and dry locations. Voltage rating is 600 volts. As an option, this cable can provided pre-pulled into duct.
Aluminum 600V URD cable has a concentric strand or compressed 1350-H19 series aluminum conductor. Conductors are cabled together, with surface printing for identification. The neutral conductor has a yellow stripe.
Aluminum 600V URD cable has a black cross linked polyethylene (XLP) insulation.
Triplex Aluminum Conductor Direct Burial 1350 Series 600V URD
It is a 600V rated cable with three aluminum conductors. Being suitable for use in direct burial, triplex aluminum conductor cable has outstanding properties to help it cope with the nature of its demanding applications. Here are some of the properties:
Aluminum 600V URD cable is made of two types of conductors: either concentric strand or compressed series of aluminum conductors. The stranded wire is more flexible and appropriate for applications that have several bends. While the compressed conductor is suitable for systems where tough cables are needed. These conductors are coupled together to improve cable integrity and the surface printed for identification purposes. Its neutral conductor always has a yellow strip.
Aluminum 600V URD cable has a cross linked polyethylene (XLP) insulation. Cross linking a thermosetting like polyethylene helps to improve its strength and versatility. For this cable to tolerate and overcome the odds that come with direct burial, it needs a reliable insulation. An insulation which is resistant to moisture, chemicals, oil, tear and abrasions.
Aluminum 600V URD is appropriate to use in establishing secondary power distribution circuits. These circuits wired using the cable can be installed either in duct or directly buried in the ground. Due to its versatility and enduring insulation, the cable works well in these applications. Even in adverse temperatures, Aluminum 600 URD triplex cable serves. It has a maximum operation temperature of 90 degrees Celsius and can work in both wet and dry places. It has a voltage power rating of 600 volts, good for medium size loads. The cable is also designed with an option, provision of pre-pulling into duct.
• ASTM B-230
• ASTM B-231
• ASTM B-609
• ASTM B-901
• ICEA S-105-692
• J-C- 30B Federal Specification
• RUS accepted
Question and Answer:
Frequently Asked Questions - Triplex Aluminum URD
Can the Triplex Aluminum URDcables be buried directly in the ground?
Yes, Triplex Aluminum URD cables can be buried directly in the ground. It can also be installed in an underground duct.It has been developed in such a way that it can be used in congested areas and is easy to install. Since it is low smoke and flame cables, it can be used both in wet and dry places.
Is TriplexAluminium URD better than copper wires?
There are more valuable reasons why Triplex Aluminium URD is better than copper.
The reasons are:
Do Triplex Aluminium URD building wires take much area than copper?
Triplex aluminium URD does take some area, even though it is lighter and weighs only half the weight than copper wires. They are compressed to bring down the size of diameter to use as an alternative tocopper. Though it takes some area, the important thingto notice is, it offers the greatest flexibility and service life than copper wires.
Is there a possibility, that during installation the Triplex Aluminium URD cables likely to get damaged?
Since Triplex Aluminium URD cables are lighter in weight than copper, it has lower pulling tension. This protects the cable from getting smudged or smeared during installation. It can withstand high elongation without any damage. Pulling tensions do not interferewith the performance of the cable. It will not de-laminate even during harsh bends. In some cases, where it has to be pulled, the use of pulling lubricants can reduce damage and lessen pulling tensions.
Does duct size matter with each Triplex Aluminium URDcable?
Yes, appropriate duct types should be used to increase performance of the cable.
Ducting can affect the pulling operation. Duct type should match the internal diameter of the duct to suit the cable. The internal finish of the installed ducting should be even to avoid cable being damaged during installation. Caution should be exercised while choosing ducts for any Triplex aluminium URD cables.