Price (Per FT.)
C-L-X Type MC cables with the impervious, continuous, corrugated aluminum sheath are recommended as an economical alternate to a wire in conduit system. They are authorized for use on services, feeders and branch circuits for power, lighting, control and signaling circuits in accordance with Articles 330 and 725 of the NEC.
CLX wire Type MC cables may be installed indoors or outdoors, in wet or dry locations, as open runs of cable secured to supports spaced not more than six feet apart, in cable tray, as aerial cable on a messenger, in any approved raceway, direct burial, or encased in concrete. CLX cable MC Type are also approved for use in Class I & II, Division 2, Class III, Divisions 1 and 2, and Class I,Zone 2 hazardous locations - NEC articles 501, 502, 503 and 505.
X-Olene® is Okonite's trade name for its chemically cross-linked polyethylene, with high dielectric strength.
Conductors are color coded using base colors and tracers in accordance with the Conductor Identification Table on the back of this Data Sheet.
Assembly and Coverings
The individual conductors are cabled together with non-hygroscopic fillers and a binder tape overall. The C-L-X sheath exceeds the grounding conductor requirements of Table 250.122 of the NEC and UL 1569. The impervious, continuous, corrugated aluminum C-L-X sheath provides complete protection against moisture, liquids and gases and has excellent mechanical strength. For direct burial in the ground, embedment in concrete, or for areas subjectedto corrosive atmospheres, the C-L-X sheath is protected with a low temperature black Okoseal® (PVC) jacket.
Conductors: Bare soft annealed copper, Class B stranding per ASTM B-8.
Insulation: X-Olene per ICEA S-73-532/NEMA WC57 and UL 44, Listed UL Type XHHW-2. Meets MIL-DTL-1377H, section 22.214.171.124.2 cold bend at -66°C and ASTM D746-04 brittle point at -76°C.
Assembly: Per UL 1569 with binder tape overall.
Sheath: Close fitting, impervious, continuous, corrugated aluminum C-L-X per UL 1569.
Exceeds grounding conductor requirements of NEC Table 250.122
Jacket: Black Okoseal (PVC) per UL requirements for Type MC Cables. Meets ASTM D746-04 brittle point at -40°C