Price (Per FT.)
Okonite Type C-L-X P-OS (Pair/Triad - Overall Shield) instrumentation cables are designed for use as instrumentation, process control, and computer cables in ITC non-classified or labeled circuits up to 150 volts and 5 amps (750VA) and in Class 2 or 3 Power-Limited circuits where shielding against external interference is required, but shielding against interference among groups is not required; indoors or outdoors; in wet or dry locations with conductor operating temperatures up to 90°C; in cable trays; in raceways; supported by a messenger wire; under raised floors; for direct burial. Suitable Class I, Division 2, Class II, Division 2, or Class III, Division 2 and Class I, Zone 2 hazardous locations. Also for use as Power-Limited protective signaling cable (FPL) per NEC Code 760.
The C-L-X sheath provides physical protection against mechanical damage. It may be installed in both exposed and concealed work, secured to supports not greater than 6 feet apart.
Conductors:Bare soft annealed copper, Class B, 7-strand concentric per ASTM B-8.
Insulation: X-Olene (XLP), UL 13 and UL Standard 2250, 15 mils nominal thickness, 90°C temperature rating.
Conductor Identification: Pigmented black and white in pairs, black, red and white in triads. Pair or triad assembled with left-hand lay.
Cable Shield: Aluminum/Polyester tape over lapped to provide 100% coverage, and a #18 AWG 7-strand tinned copper drain wire.
Inner Jacket: Black, flame-retardant Okoseal (PVC) per UL 13 and UL Standard 2250. A ripcord is laid longitudinally under the jacket to facilitate removal.
C-L-X Jacket: A close-fitting, impervious, continuously welded and corrugated aluminum sheath provides complete protection against moisture,liquids, and gases, has excellent mechanical strength and provides equipment grounding through the sheath.
Outer Jacket: Black, flame-retardant low temperature PVC Okoseal per UL Subject 13 and UL Standard 2250.
UL Listed as Type ITC/PLTC — Instrumentation Tray Cable/Power Limited Tray Cable for use in accordance with Article 727 and Article 725 of the National Electrical Code.
These cables comply with UL 2250 and UL 13 for PLTC, CL2 and CL3.