Price (Per FT.)
Loxarmor power cables are recommended as an economical alternate to a wire in conduit system. They are designed specifically for use as feeders in industrial and utility power distribution systems. Loxarmor power cables may be installed in both exposed and concealed work, wet and dry locations, direct burial in the earth or embedded in concrete. They may be installed on metal racks, troughs, in cable trays or secured to supports not greater than 6 feet apart.
Loxarmor power cables are also approved for Classes I and II, Division 2, and Class III, Divisions 1 and 2, hazardous locations - NEC Articles 501, 502 and 503.
Okoguard Is Okonite's registered trade name for its exclusive ethylene-propylene rubber (EPR) base, thermosetting compound, whose optimum balance of electrical and physical properties is unequaled in other solid dielectrics. Okoguard insulation, with the distinctive red color and a totally integrated EPR system, provides the optimum balance of electrical and physical properties for long, problem free service.
The Type MV-105 conductors are assembled with fillers and a binder tape overall. One bare stranded copper grounding conductor is placed in one of the outer interstices. The interlocked Loxarmor provides excellent mechanical strength. For direct burial, embedment in concrete or for areas subjected to corrosive atmospheres, the Loxarmor is protected with a red Okoseal® (PVC) jacket.
Conductors: Uncoated copper compact stranded per ASTM B-496.
Strand Screen: Extruded semiconducting EPR strand screen meets or exceeds electrical and physical requirements of ICEA S-96-659/NEMA WC71 and UL 1072.
Insulation: Okoguard meets or exceeds the electrical and physical requirements of ICEA S-96-659/NEMA WC71 and UL 1072. The insulated conductors are tested in accordance with AEIC CS8.
Insulation Screen: Extruded semiconducting EPR insulation screen per ICEA
S-93-639/NEMA WC74, AEIC CS8 and UL 1072.
Shield: 5 mil uncoated copper tape helically applied with 12.5% nominal overlap.
Phase Identification: Color coded (black, red, blue) polyester ribbon laid longitudinally under the copper shield tape.
Grounding Conductors: Three uncoated copper Class B in accordance with UL 1072.
Assembly: Cabled with fillers and ground wires, in the interstices, binder tape overall.
Loxarmor: Galvanized steel or aluminum interlocked tape armor per UL 1072, ICEA S-96-659 NEMA WC71, and UL Listing E-60545.
Jacket: Sunlight resistant red PVC jacket in accordance with UL 1072.
UL Listed as Type MV-105 or MC, sunlight resistant, for use in cable tray, and for direct burial in accordance with UL 1072.
Cables listed to CSA C68.3 are also available..