Price (Per FT.)
Okoguard shielded Okolon TS-CPE Type MV-105 power cables are recommended for use as feeder circuits in electric utility generating stations, for distribution circuits, and for feeders or branch circuits in industrial and commercial installations.
Type MV cables may be installed in wet or dry locations, indoors or outdoors (exposed to sunlight), in any raceway or underground duct, directly buried if installed in a system with a grounding conductor in close proximity that conforms with NEC Section 250.4(A)(5), or messenger supported in industrial establishments and electric utilities. Sizes 1/0 AWG and larger may also be installed in cable tray.
Okoguard is Okoniteâ€™s registered trade name for its exclusive ethylene-propylene rubber (EPR) based, thermosetting compound, whose optimum balance of electrical and physical properties is unequaled in other solid dielectrics. Okoguard insulation, with the distinctive red color and a totally integrated EPR system, provides the optimum balance of electrical and physical properties for long, problem free service.
The triple tandem extrusion of the screens with the insulation provides optimum electrical characteristics.
The Okolon TS-CPE jacket on this cable is a vulcanized chloronated polyethylene base compound which is mechanically rugged, flame, radiation, and oil resistant.
Conductor: Annealed uncoated copper compact stranded per ASTM B-496.
Strand Screen: Extruded semiconducting EPR strand screen. Meets or exceeds electrical and physical requirements of ICEA S-93-639/NEMA WC74 & S-97-682, AEIC CS8, CSA C68.3 or UL 1072.
Insulation: Meets or exceeds electrical and physical requirements of ICEA S-93-639/NEMA WC74 & S-97-682, AEIC CS8, CSA C68.3, and UL 1072.
Insulation Screen: Extruded semiconducting EPR insulation screen. Meets or exceeds electrical and physical requirements of ICEA S-93-639/NEMA WC74 & S-97-682, AEIC CS8, CSA C68.3 and UL 1072.
Shield: 5 mil bare copper tape helically applied with 25% nominal overlap.
Jacket: Meets or exceeds electrical and physical requirements of ICEA S-93-639/NEMA WC74 & S-97-682, CSA C68.3 and UL 1072 for chloronated polyethylene jackets.
UL Listed as Type MV-105, sunlight resistant and for use in cable tray in accordance with UL 1072.
CSA C68-3 listed and rated FT4 (1/0 and larger) and -40Â°C.